Investigation of Leakage on Water Wall Tube in a 660 MW Supercritical Boiler
type: Post
type: BlogPost
modified: 2015-11-17
created: 2015-03-11
link: https://lib.itenas.ac.id/kti/
has creator: account
has container: posts
encoded: The leakage of a supercritical boiler tube has been investigated. The leakage was observed during a working pressure hydrostatic test under 40.1 MPa. The internal geometry of the investigated leaking tube was multi-lead ribbed tube. Various methods for investigation namely radiography, microstructural analysis using optical and scanning electron microscopes, Vickers hardness testing and chemical analysis were conducted to investigate the main cause of leakage. The results revealed that the material tube met the standard for supercritical boiler tube (ASTM A 213 Grade T12). From the microstructural analysis, there was a crack, which initiated from the outer wall adjacent to the weld metal and propagated to the inner wall of the tube. The crack was due to a weld defect known as “excessive melt through” which is due to overheating during the welding process in joining the tubes. It is suggested that control of welding process parameters must be accomplished during fabrication to make a furnace wall, and placing strip of steel between the tubes to reduce the fit-up gap should be considered. Dibuat oleh : Meilinda Nurbanasari, Abdurrachim E-mail: meilinda@itenas.ac.id Kata Kunci : Supercritical boiler tube, Leakage, Multi-lead ribbed tube, Microstructure Keterangan : Makalah ini dimuat pada Journal of Failure Analysis and PreventionOctober 2014, Volume 14, Issue 5, pp 657-661 Investigation of Leakage on Water Wall Tube in a 660 MW Supercritical Boiler
content: The leakage of a supercritical boiler tube has been investigated. The leakage was observed during a working pressure hydrostatic test under 40.1 MPa. The internal geometry of the investigated leaking tube was multi-lead ribbed tube. Various methods for investigation namely radiography, microstructural analysis using optical and scanning electron microscopes, Vickers hardness testing and chemical analysis were conducted to investigate the main cause of leakage. The results revealed that the material tube met the standard for supercritical boiler tube (ASTM A 213 Grade T12). From the microstructural analysis, there was a crack, which initiated from the outer wall adjacent to the weld metal and propagated to the inner wall of the tube. The crack was due to a weld defect known as “excessive melt through” which is due to overheating during the welding process in joining the tubes. It is suggested that control of welding process parameters must be accomplished during fabrication to make a furnace wall, and placing strip of steel between the tubes to reduce the fit-up gap should be considered. Dibuat oleh : Meilinda Nurbanasari, Abdurrachim E-mail: meilinda@itenas.ac.id Kata Kunci : Supercritical boiler tube, Leakage, Multi-lead ribbed tube, Microstructure Keterangan : Makalah ini dimuat pada Journal of Failure Analysis and PreventionOctober 2014, Volume 14, Issue 5, pp 657-661 Investigation of Leakage on Water Wall Tube in a 660 MW Supercritical Boiler
topic: https://lib.itenas.ac.id/kti/